Transformers are of great help in terms of electricity. They can fully convert electricity and ensure the normal operation of power projects. Next, Shenzhen Zhongji Electric Technology Co., Ltd. will introduce the installation conditions of the transformer.
Transformer installation conditions:
1. The altitude does not exceed 1000m
2. Ambient temperature: highest temperature +40℃, highest daily average temperature +30℃, highest annual average temperature +20℃, outdoor lowest temperature -30℃, indoor lowest temperature -5℃.
3. For non-enclosed transformers, a fixed fence with a height of not less than 1.7m should be installed, and the mesh of the fence should not be larger than 40mm×40mm. The net distance between the outside of the transformer and the barrier should not be less than 0.6m, and the net distance between the two transformers should not be less than 1.0m. The dry-type transformer can be directly installed on the foundation, the small wheels are removed, and the IP20 shell is fixed with a bolt. It is suitable for indoor use. It is made of 12mm mesh aluminum alloy plate, which can prevent foreign objects from entering and provide a safety barrier for live parts.
4. The outer casing of the transformer is used outdoors and is made of a mesh aluminum alloy plate with a 60° angle to the straight line to prevent the inflow of water droplets. This kind of casing will reduce the cooling capacity and reduce the output capacity of the transformer by 5% to 10%.